Compact, flexible design is NEBS Level 3 certified compliant and ideal for telecommunications facilities requiring modular battery plants.
The NetSure Battery Stand provides capacities ranging from 150 to 1860 amp-hours per bay for +24V applications and 150 to 930 amp-hours per bay for -48V applications. Model 24BA1200 (+24VDC) and model 48BA1200 (-48VDC) battery stands mount VRLA batteries in 2 to 4 tiers with a rectangular footprint 25"W x 23"D. Larger capacity requirements are filled by 5 and 6 tier systems with a rectangular footprint of 25"W x 26"D. Systems with four battery shelves or less can be equipped with the modular NetSure VPS mounted above the batteries providing a complete DC power plant in one bay. The NetSure VPS is equipped with a MCA to control and monitor battery recharge current and low voltage battery disconnect, as well as measure battery discharge current. Battery life is maximized through monitoring and controlling battery voltage and current during charge cycles.
The NetSure Battery Stand is designed for use in wireline and wireless communication systems installed in small offices, huts, CEV’s and CUE’s. It is also designed for use with the NetSure VPS and is compatible with most DC power equipment.